Figure 1. The Wye service transformer has three 120-V windings, which are 120 degrees apart.
Wye or “star” service transformers are one and the same. The names come from the secondary winding configuration, which looks like a “Y” or three-sided star (Figure 1). For the remainder of this article, the term “Wye” will be used to describe this transformer’s secondary windings.

(My March 3, 2003 column dealt with the secondary windings of a Delta service transformer, showing that power-leg or wild-leg voltage is 208 V with respect to ground. It also mentioned that this 208 V should not be confused with the 208 V coming from the secondary Wye service transformer.)

This article will deal with the secondary windings of the Wye service transformer.

Wye service is probably one of the most popular service drops in medium-size commercial buildings. This dual-voltage, three-phase service delivers four wires to the building. There are actually three 120-V windings, which are 120 degrees apart (Figure 1). They consist of three hot wires and a neutral or “ground.”

The secondary winding of the Wye is center-tapped and grounded. This makes the center tap, or ground, perfectly symmetrical to all three phases of its power.

There is no “wild” or “power” leg in the Wye configuration, as there is in the Delta transformer’s center-tapped secondary (described in the March 3 article).

Figure 2. Single-phase voltages can be picked off of the Wye secondary.

## Voltages

Wye service can be used for three- and single-phase applications. Single-phase voltages can be picked off of the Wye secondary (Figure 2). Listed here are those single-phase voltages:

• A to B – 208 V;

• B to C – 208 V;

• A to C – 208 V;

• A to N – 120 V;

• B to N – 120 V; and

• C to N – 120 V.

As we can see, 120-V single-phase, 208-V single-phase, and 208-V three-phase power can be had from the Wye when it is center-tapped to the ground. The 208-V three-phase power comes from the use of all three power legs, A, B, and C. If the Wye were not center-tapped to ground, no low-voltage (120-V) single-phase power would be available. However, 208-V single-phase and 208-V three-phase power still would be available without the center-tap. The 208-V single-phase power would come from any two power legs — A and B, B and C, or A and C (Figure 2).

It can be said that any two of the three windings of the Wye secondary are in series with one another (Figure 2). However, remember that power surges of the inducted voltage that come from the primary windings to the secondary windings are not in phase with one another. In fact, each phase is 120 degrees out of phase with one another (Figure 3).

When one phase is positive and maximum voltage, the voltages of the other phases or windings may be negative and less than maximum. The phenomenon makes the voltage between any two conductors to be 208 V and not 240 V (120 V x 2) (Figure 2).

Figure 3. A chart of time versus voltage. Note that each phase is 120 degrees out of phase with one another. (Courtesy of McGraw Hill.)

Notice that the neutral or ground wire is connected to the center of the Wye, which makes it perfectly symmetrical. The voltage between any phase (A, B, or C) and neutral (N) will be 120 V.

Since there is no wild leg or power leg as in the Delta service transformer, all 120-V, single-phase loads may be connected to N and any of the three power wires, A, B, or C, without worrying about “burning them out” from too high of a voltage.