A successor to MicroPump I, the MicroPump II micro condensate pump is 48 millimeters shorter than the previous model. It will fit inside the tubing chase of high-wall-mount a/c units. The pump now has an internal filter, thus saving space. It has a discharge rate of up to 12 liters per hour. Vertical discharge is up to 15 meters and horizontal discharge is up to 100 meters. The single package pump has no float, which can sometimes stick and cause problems, says the company. Features include a transparent filter chamber and a one-quarter-turn twist to allow the chamber to be easily removed from the filter and washed. The AquaSensor, which has no moving parts and gives much more freedom in positioning the pump, can be operated horizontally or vertically. The Excess Water Alarm relay circuit can be connected to a building management system or can shut down the air conditioner if the water level is too high. The power supply is 208-240V 50/60Hz or 110-120V 60Hz.
EDC International Inc., 315 Riggs St., Unit 1, Oxford, CT 06478; 203-881-5544; 203-881-2644 (fax); email@example.com