Bob and Tim have arrived at the apartment house that they have been working at for the last several days. They’ve gone to the roof where the outdoor units are located. There are 60 heat pumps that use R-22 as the refrigerant. They start with Unit No. 2.
Bob and Tim are on the second day of an inspection of an apartment house building that has multiple split-system heat pumps. They have inspected all 60 outdoor units on the roof. They are now going to inspect the indoor units.
Bob and Tim have arrived at Tim’s first service call. Tim asked Bob, “What is this call all about?” Bob said, “This is a new customer that wants us to take over the maintenance work for this apartment house.”
Btu Buddy has met Bob for lunch to answer some questions that Bob had about yesterday’s service call. Bob asked, “Why did that motor have two contactors and so many wires going to it? It seemed very confusing. I am glad that I tagged those motor leads when I disconnected the motor. I never would have figured out how to reconnect the leads.”
Bob got a call to go to a convention center where the air conditioning system was not working. It was a 75-ton unit with one compressor. The system was many years old, but had been functioning fine, until now. After checking out the unit, an ohm check showed 0 resistance to ground.
Bob has received a call from the dispatcher about a system that is not cooling. The job is a small building with a 5-ton cooling unit. Bob went to the outdoor unit. It was running and all appeared normal. He went to the truck to get his gauges, and when he got back, he noticed that the compressor didn’t seem to be running.
Bob has been sent on a service call where the customer is complaining about her power bill. She thinks that the heat pump may be the problem. Her power bill is much higher than last year. She explained this to Bob and he started by asking a question, “Does the auxiliary heat light come on very often on your thermostat?”
Bob and Btu Buddy were on a service call yesterday where the compressor motor was running overloaded due to internal load; the bearings were dragging or worn. Btu Buddy told Bob, “Motor overload protection and circuit protection are subjects that need to be discussed later.” They’ve gotten together today for that discussion.
Bob got a call from the dispatcher to go to an office building that has a 3-ton heat pump compressor that has been shutting off after startup. The fan would continue to run. The building maintenance man said that he had observed the shutting down of the compressor several times.
Bob has gone on a service call where the customer is complaining that her house is not getting up to temperature. The house was heated with a heat pump with three stages of auxiliary strip heat. Bob removed the panel to the strip heat and found one of the units was not pulling current.