Since the tax credit program became available, all types of geothermal options have been on the minds of the building community. The earth loop, often referred to as the refrigerant loop, may be installed in three different configurations: diagonal, vertical, and horizontal.
Many servicemen experience service calls where the compressor has both a low head pressure and a high suction pressure. There are three main reasons why a compressor will simultaneously have a low head pressure and a high suction pressure.
For this column I want to discuss a real life situation regarding poor cooling in a residence and reduced airflow coming from the registers in the house. The air conditioner is a three ton (36,000 btuh), HCFC-22, split type, air conditioner with the A-coil in the plenum of the furnace located in the basement.
The condenser is the component that rejects the heat from the system. Most equipment is air cooled and rejects heat to the air. The coils are copper or aluminum and both types have aluminum fins to add to the heat exchange surface area.
Ferris State University’s Commercial Refrigeration Laboratory has gone totally chlorine-free. By replacing the refrigerant HCFC-22 that was in two medium-temperature commercial refrigeration cases in the laboratory, the students in the associate degree program in HVACR can boast that the lab is now chlorine-free.
This column focuses on condenser splitting. But first, here’s a quick review of condenser flooding before covering condenser splitting to help all better understand both concepts and their advantages and disadvantages.
This article is part two of a two-part series on ice flake machine troubleshooting. The last article, which appeared in the Feb. 7 NEWS, examined troubleshooting low and high water levels. This article will examine water impurities and mechanical problems.
My Feb. 7 column focused on ice flake machine troubleshooting. I will have more to say on that specific topic in my April 4 column. For this column, I want to take a look at amperage as it relates to HVACR compressors.