Service & Maintenance
November 8, 2010
When the customer calls for service, he tells you that when things got very cold in the house, he disconnected the power supply to the unit, and then, after turning the 120-volt service switch back on, the operation seemed normal and the house got warm “for a day or so.” But the failure repeated.
October 18, 2010
Bob’s service call yesterday involved a leaking underground refrigerant piping system. Bob replaced the refrigerant lines, leak tested the lines, and left them yesterday afternoon under 150 psig of pressure. He has now returned to the job the next day to see if the pressure held and to check for moisture in the system.Read More
October 4, 2010
For several years, refrigerant retrofitting has been a common procedure for a lot of the commercial kitchen and restaurant equipment I work on, so I’ll go over some of the things I’ve learned that might help you save some time and money on your own retrofit projects.
September 20, 2010
Bob was called to a job that had a no cooling complaint. This was
a new customer and Bob wanted it to be a good experience for the customer. It
was a small stand-alone store building with a 3-ton cooling only unit. Bob determined this was a low charge problem. He installed his gauges and discovered the
unit did not have any refrigerant in it.Read More
September 6, 2010
In this troubleshooting situation, we have a customer who has called to say that their 12,000 Btu through-the-wall unit is “blowing cool air even though it’s set for heat.” The unit is a heat pump with a three-speed motor. It operates on 240 vac.
August 23, 2010
The dispatcher called Bob and sent him to a job that really sounded like a problem. There had been a hard rain and a customer had a condensing unit that had been under water that morning due to high water from a creek behind his house. The owners were on a fixed income and wanted to get the repair at the best possible price.
August 9, 2010
Fire and smoke dampers are a proven and effective way to protect duct and air-transfer openings in walls, barriers, partitions, corridors, and shafts. This article includes the basic testing, installation, and maintenance requirements for life safety dampers.
July 19, 2010
Bob has been on a job at a convention center with a 100-ton water cooled condenser. The owners are anxious for Bob to get the a/c back on, but Bob said the tubes must be cleaned before the unit will run. He has called the shop and asked for a helper and a tube cleaning machine to help him get the unit running as fast as possible.
July 5, 2010
Your role in this month’s troubleshooting situation is as the follow-up technician on a problem that was made worse by the technician who preceded you. When the restaurant manager originally called for service, the complaint was that their small walk-in cooler “wasn’t keeping as cool as usual.” Now it’s “hardly cooling at all.”
June 21, 2010
The dispatcher calls Bob with an urgent service call from the city’s convention center. A convention is going on and the air conditioner is off, and it re-starts but only runs a short time and shuts off again. The maintenance man said he had to reset the high pressure control to get it started. Btu Buddy assists in troubleshooting the system.