Bob and Tim were on their way to a no cooling call at an office building with a 100-ton water-cooled chiller. As always, management was in a hurry to get the problem solved because the tenants were hot.
Looks at Whether Retailers Save Money by Minimizing Risk of Equipment Failure and Reducing Service Calls
June 9, 2014
Alpine Mechanical Services has announced the completion and results of a collaborative energy efficiency study on rooftop units conducted by Alpine Mechanical, Siemens Industry, and Nexant. The study tested the efficacy of HVAC preventative maintenance best practices in a retail environment.
Bob and Tim were on their way to a no cooling call. The spring season was still cool at night and warm in the daytime. The customer told the dispatcher, “The unit started up at about 10:30 a.m. this morning and made a noise, but did not cool the house, even though it is still running.”
In this month’s troubleshooting situation, our customer’s description of the problem is “not cooling” and “blowing warm air,” and the equipment that is supposed to keep this residence comfortable is a split system that has been in service for 16 years.
Bob and Tim were on their way to a no cooling call, their first of the season, when Tim asked, “Wonder why we would have a no cooling call this time of year? It is only 75°F during the day and 40° at night.”
For the HVACR technician, the right tool for soldering and brazing pipe — an air-fuel or oxy-fuel torch — depends on the type and diameter of the pipe, its location, and considerations related to cost, safety, convenience, and ease of use. This article will examine those factors, as well as clarify some technical issues.
Tim had asked Bob to go into depth about tuning an oil burner during the last service call. “You said that oil burning equipment requires more attention than any other type of residential heating equipment,” Tim said. “Can you explain why?”
Looking ahead to the upcoming cooling season, the equipment in this troubleshooting situation is a split system that’s approximately eight years old, consisting of a gas furnace that provides heat in the winter and a condensing unit and A coil to provide summer cooling.
Bob and Tim were on their way to an oil heat service call. It is cold and the owner has no heat. Tim read the service ticket for today and said, “The owner says that the burner won’t burn and makes a sputtering sound for a few minutes and shuts off.”
One of the most common furnace problems that I see is when the furnace hot surface ignitor will not glow. The furnace may have a bad ignitor, loose wire connections, open limit switch, open rollout switch, open pressure switch, or bad control board. This is what you might see in the furnace sequence of operation.