Bob and Tim were on their way to do routine annual service on a customer’s gas furnace and humidifier. Tim asked, “What are the things that we should look for that may cause problems on a gas furnace?”
Your troubleshooting problem involves a 3-ton split system, and the complaint is that in a high outdoor ambient situation, the unit is unable to obtain the necessary comfort level in the 1,200-square-foot building it is supposed to cool. And, this unit has a history.
Bob and Tim were at the shop after a day of service calls. The weather was still hot, 93°F, and Bob said, “We just did a service call with a system that was overcharged and had an orifice expansion device. I would like to go into further details with you on a system with a thermostatic expansion valve (TXV) for an expansion device.”
Homeowners Are Looking for Ways to Save Energy and Money; Here’s How HVAC Professionals Can Help
October 6, 2014
Homeowners want ways to save energy and cut costs. HVAC contractors are looking for new business opportunities. And technologies like thermal imaging enable you to see and do more than ever before. Why not bring customer needs, technology, and your skills together by offering home energy audit services? Here’s how.
Bob and Tim were on their way to a service call with a new customer. When they got to the job, the customer explained, "The unit was not cooling and I had a company come out for a service call. The unit seemed to work OK last week when it was a little cooler outside, but this week it has warmed up and the unit is not functioning as well."
Your troubleshooting situation involves a standard natural gas, induced draft, hot surface ignition system furnace. This is a new installation that has been accomplished in anticipation of the upcoming heating season, and the problem is that during the initial start-up the unit did not perform properly.
Bob and Tim were on their way to a no cooling call; in fact, it sounded like a heating call. The customer has a bonus room on the third floor that used to be attic space. When Bob and Tim arrived, the customer told them, “The bonus room upstairs seems much too hot and the air coming out of the registers is hot to the touch.”
Live Active Leisure needed to replace its existing system due to the legally imposed phaseout of HCFCs in the United Kingdom. Johnson Controls proposed the installation of an air-cooled ammonia chiller complete with heat recovery and a very low ammonia charge due to the location being close to a pedestrians’ footpath.
A Well Maintained Unit Will Continue to Function at the Original Optimum Efficiency
August 4, 2014
Save up to 15 percent on electricity costs with these simple preventive maintenance tips for cooling tower. Routine maintenance also helps to conserve water and extend the operating life of cooling equipment.
Bob and Tim were getting set up to clean the condenser tubes in a chiller. They were doing this job at night during overtime hours because they discovered the problem earlier that afternoon and the customer said the chiller needed to be able to operate at full capacity tomorrow for a conference.