Replacing a compressor is neither simple for a technician nor inexpensive for the customer. Before replacing a compressor, a technician needs to ensure that it is truly defective. Unfortunately, sometimes good compressors get replaced as a result of a misdiagnosed problem.
When a refrigeration system fails, many times the cause can easily be diagnosed. However there are occasions when the cause cannot easily be determined - either the true cause is unclear or the technician is unsure of a problem. How do you work through these jobs? One method used by some techs is to “read and record.”
Actually, frost on the suction line only indicates that at the location where the frost is present, the suction line piping is below the dew point temperature of the surrounding ambient air and at or below 32°F. That’s it. It is neither an indication of a properly operating system nor a system defect.
The process of brazing ACR tubing is a common task for many refrigeration technicians. Although this is relatively simple, there are some system problems that can occur if some basic brazing procedures are not followed.
Accurately troubleshooting and repairing refrigeration systems requires technicians to use many specialty instruments. They base many of their diagnoses on what is read from these instruments. Relying on them to be consistently accurate day in and day out is a must. If these tools are inaccurate, more than likely the diagnoses will be inaccurate.
While repairing refrigeration equipment, technicians sometimes come up with unique methods of solving problems. Many of these are used again and again and become known as “tricks of the trade.” When a bunch of technicians get together, they oftentimes enjoy sharing new tricks they learned or developed recently. It’s like a badge of honor.
When multiple compressors are piped together with a common
suction and discharge header - such as with the arrangement of a parallel rack
configuration - oil return to each compressor is a major concern. Typical oil
recirculation rates are dependent on three factors.
The actual frequency and tasks performed will vary from system to system. However, here are some generic maintenance tasks which can be applied to many refrigeration systems. These tasks can be divided into two groups: one for maintaining the cabinet and one for maintaining the refrigeration system.
We all, at one time or another, come upon a system that is quite difficult to repair or to troubleshoot. This can be a very stressful experience. Different technicians have different ways of handling this stress. Some throw tools. Some talk to themselves. A better way of handling this stress is to first take a break.
Refrigeration systems utilizing an outdoor air-cooled condenser located in an area where the outdoor temperature can drop below approximately 70°F must be designed to prevent the system’s discharge pressure from dropping too low. There are several different methods that can be used to accomplish this task.