Bob and Tim are continuing a service call on a heat pump that has two failed auxiliary heaters. When they went to the supply house to get new heaters, they left wondering if the heat pump itself was operating up to capacity. After replacing the defective heaters, Bob suggested a visual inspection of the heat pump.
Bob and Tim have arrived at a home where the owner is complaining that the heat pump is not heating properly. It has been getting cold in the home during the late night and early morning hours. It’s really cold outside, about 10°F at night and 25° during the day.
Tim and Bob have been sent on a service call to a new customer’s house. The homeowner has an unusual complaint. She said that she thinks she has a furnace problem because there is mold in her house. They don’t know what this can be all about.
Bob and Tim have arrived back at the apartment building where they have been working for several days inspecting and making necessary repairs to the building’s split-system heat pumps. Bob said, “Check the list for another unit that seemed to have a problem and let’s take a closer look at it.”
Bob and Tim have arrived at the apartment house that they have been working at for the last several days. They’ve gone to the roof where the outdoor units are located. There are 60 heat pumps that use R-22 as the refrigerant. They start with Unit No. 2.
Bob and Tim are on the second day of an inspection of an apartment house building that has multiple split-system heat pumps. They have inspected all 60 outdoor units on the roof. They are now going to inspect the indoor units.
Bob and Tim have arrived at Tim’s first service call. Tim asked Bob, “What is this call all about?” Bob said, “This is a new customer that wants us to take over the maintenance work for this apartment house.”
Btu Buddy has met Bob for lunch to answer some questions that Bob had about yesterday’s service call. Bob asked, “Why did that motor have two contactors and so many wires going to it? It seemed very confusing. I am glad that I tagged those motor leads when I disconnected the motor. I never would have figured out how to reconnect the leads.”
Bob got a call to go to a convention center where the air conditioning system was not working. It was a 75-ton unit with one compressor. The system was many years old, but had been functioning fine, until now. After checking out the unit, an ohm check showed 0 resistance to ground.
Bob has received a call from the dispatcher about a system that is not cooling. The job is a small building with a 5-ton cooling unit. Bob went to the outdoor unit. It was running and all appeared normal. He went to the truck to get his gauges, and when he got back, he noticed that the compressor didn’t seem to be running.