A VFD bypass assures the customer uninterruptible operation with their HVAC system - the ability to keep their fans and pump running at all times - even if the drive is taken out of the loop for whatever reason.
This requirement could be needed for a multitude of reasons, but the most common ones include reprogramming or servicing of the drive, or in the rare event of the drive mechanically failing. In the early days of drives, back some 20 years ago, their failure rate was an issue. However, today it is rare for any drive to just mechanically fail. The requirement for a bypass is also critical in applications that demand essential services and smoke purge capabilities, where it is imperative that the motor runs to destruction if necessary.
The bypass enclosure itself is also used to house additional customer required components like line or load reactors and other devices for circuit protection. Line and load reactors are used for conditioning of the power. The other components facilitate the isolation and switching of the control devices.
Up until a few years ago, the only bypass option available to customers was a conventional bypass package. An electronic, intelligent bypass solution did not exist.
A conventional bypass incorporates pushbuttons, selector switches, and indicator lights to accomplish its primary functions. In comparison to an electronic bypass, though, a conventional bypass is somewhat limited in capability and function. In addition, a tremendous amount of point-to-point wiring is needed to wire up control relay devices and components in a conventional bypass. The more point-to-point wiring used, the greater probability of reliability and troubleshooting problems occurring down the line.
A popular feature is interlock start logic, or built-in damper end switch relay logic. With the interlock start logic feature, a related damper will open, and the damper's end switch will then tell the drive's bypass that it is safe to start the motor. Other electronic bypass features include multiple relay outputs, inputs, safety inputs, common remote start/stop, LED indicators, auto bypass, essential services mode, disconnect options, and more.
For the engineering spec, there is no reason not to go with an electronic bypass for its advanced capabilities alone. In addition, the prices of either the conventional bypass or electronic bypass are essentially the same. Presently there are only four VFD manufacturers that offer electronic or intelligent bypass solutions.
A particular feature or requirement may not be known, or may be overlooked by the installer at the jobsite, which could result in having to remove, reconfigure, and then reinstall the bypass. Make sure the VFD installers are certified by the manufacturer to get the most out of the drives' capabilities. Finally, make sure the drives are specified with advanced features as well, such as an integral harmonics reduction capability, which eliminates the need for line reactors to reduce harmonics problems.
Reprinted with permission from the Siemens Building Technologies white paper "VFD E-Bypass 101: The Basics." For more information, visit www.sbt.siemens.com/hvp/components.
Publication date: 03/08/2004