The capacity in Btuh can be calculated, determining if the unit is working at or near capacity, with a psychrometric chart, digital thermometer, digital humidity stick, and an accurate method to calculate airflow.
The Air-Conditioning and Refrigeration Institute (ARI) defines the standards for air conditioning operational design. All equipment in the ARI directory is rated under the same conditions.
Design conditions are shown in Table 1.
At these conditions, almost all (there is always the one exception) standard efficiency air conditioners operate with a 40 degrees F evaporator coil and at 125 degrees condensing temperature. Information on other types of systems can be referenced in the equipment design section. Your distributor or the manufacturer can tell you at what conditions the equipment was rated. For the rest, physics is physics and the rules don't change.
Airflow should never be set by measuring temperature drop across the evaporator coil. Setting the airflow is easy. There are several ways to do so. The easiest way is using the static pressure drop across the dry coil. Look in the coil manufacturer's literature. With a digital manometer and a chart, airflow can be set across a dry coil in a matter of minutes.
Airflow should be 400 cfm per ton:
To further understand how to check the charge without gauges, let's work from design conditions. Say the indoor temperature is 75 degrees and the coil temperature is 40 degrees. The design temperature difference is 35 degrees. This temperature difference will stay the same under all load conditions at the rated cfm.
The temperature difference is dependant upon the manufacturer's design. A high-efficiency evaporator is larger, and the refrigerant may boil at a temperature difference of 30 degrees, or a 45 degrees coil when the space temperature is 75 degrees. The design temperature difference, if not given by the manufacturer, can be calculated and recorded during the installation provided the airflow and charge are set correctly using the manufacturer's data. This is commonly called benchmarking. The exact boiling temperature depends upon the manufacturer and how large the evaporator coil is.
Using a digital manifold set with data logging provides the additional value of having a permanent record of equipment operation and operating characteristics, allowing a future service person to determine if any operational changes occurred that could affect system performance. As SEER ratings change, we can expect to see the operation of the equipment change, and proper charging techniques will become more critical than ever. Keep this point in mind for later.
The RA dry bulb temperature minus the design temperature difference equals the saturation temperature of the evaporator coil. Add the required superheat and you have the required suction line temperature. If the temperature is Â±2 degrees, the charge is OK.
Measure the suction line temperature at the evaporator coil outlet.
75 degrees RA â€“ (35 degrees design temp difference) = 40 degrees evaporator coil.
40 degrees + (8 degrees-10 degrees superheat) = 48 degrees-50 degrees suction line temperature.
Â±2 degrees = 46 degrees-52 degrees acceptable line temperature range.
If the system falls outside of the 2 degree range, it's time for further investigation. It's probably time to hook up the gauges, but again, you need to know what the pressure should be.
Using a charging calculator, you can determine that the superheat should be 8 degrees to 10 degrees. If the metering device were fixed, the superheat would be 10 degrees, meaning the suction line temperature would be 48 degrees to 52 degrees. If the line is too cold or too hot, verify conditions that were used in the superheat calculation. If the humidity is low, the load will be low also.
Make sure the system was installed with matched components. Cooling systems are designed to operate within design parameters, and to reach their rated efficiency, with matched components. A mismatched system may cool, but that doesn't mean it will cool efficiently or effectively.
Look at the ARI equipment directory to see how the equipment was rated for the evaporator coil installed on it. This information is available from your distributor. Sometimes systems are designed specifically to remove latent or sensible heat, and the design temperature difference will change.
Remember, 400 cfm/ton is the nominal airflow; lower airflow will give a higher temperature difference due to the colder coil temperature, and higher airflow the opposite. If you live in an area where the airflow is more or less than the nominal (e.g., Arizona systems require 450 cfm/ton due to the low humidity), you will use a different design temperature difference.
Keep in mind that you will only have to do a lot of these things once. Airflows do not change substantially with proper maintenance; the components won't change; and the system is a sealed system. If this information is documented after the initial installation or service, it will become an invaluable record, and a documentation of proper performance for you and your customer.
At a nominal cfm, all evaporators must have similar operating characteristics to remove the same amount of heat from the same amount of air under the same load conditions. It comes down to physics: time, temperature difference, and turbulence. In order to remove the same amount of heat, the refrigerant's boiling temperature must be the same across the board.
Condensers, on the other hand, do not always follow conventions. Manufacturers will differ in the compressor selection, metering device, required subcooling, and temperature rise, according to their own design to meet capacity and energy use requirements. In practice it is best to benchmark condenser performance at installation if the manufacturer's information is not available, to make future evaluations of condenser performance.
All information pertaining to the sealed system's performance can be accurately evaluated using temperatures alone with knowledge of design. A thorough understanding of system design and field practice of benchmarking systems will save time, increase equipment life, and reduce refrigerant emissions.
Last but not least, if you are going to hook up gauges, consider going digital. A refrigeration analyzer (like the Testo 523), along with a few other digital tools, will not only allow you to set up equipment with laboratory accuracy, it will also decrease your time for service, reduce callbacks, increase professionalism, and provide a service to your customers that exceeds anything your competition is currently offering.
As a service tech, manufacturer's rep, maintenance technician, or lab test technician, you will have a window into the system, allowing you to see what you haven't been able to see before. You will be able to more accurately diagnose problems, spot trends, and see what you have been missing. Technology can make your results better and your life easier.
Publication date: 10/24/2005