In order to install and service the increasing number of 410A unitary air conditioners and heat pumps continuing to enter the market, large numbers of contractors have sought training. Some of it is specific to 410A systems, but much of it is just good service practice that should be applied to any unitary system.
R-410A will also produce refrigerant burns more quickly than R-22. Protective equipment is a vital part of safe work practices.
R-410A refrigerant must be removed from the drum in a liquid state. The two refrigerants that comprise it boil at close to the same temperature. Therefore, for slight leaks, R-410A can be topped off. Just make sure it's removed from the drum while it is in a liquid state.
If you are charging it into the low side of the system, remember that the liquid must be vaporized before it enters the suction line. Then check the system's performance.
When in doubt, recover all the refrigerant and recharge the system.
POE oils have a much greater affinity for water; if a system is left open and air gets in, the moisture in the air condenses and the moisture gets into the oil. POEs plus moisture creates acids and sludge that damage the system.
In addition to not leaving the system open unnecessarily, contractors and technicians should take the following new installation precautions so that condensation cannot get into the oil:
Because of problems with condensation, sloppy installation techniques on 410A systems can lead to many callbacks, and the use of several driers to clean and dry the system. In short, the callbacks can eat up the profits from the job.
For more information, click on the Emerson Climate Technologies logo above.