Bob got a call from the dispatcher to go to an office building that has a 3-ton heat pump compressor that has been shutting off after startup. The fan would continue to run. The building maintenance man said that he had observed the shutting down of the compressor several times.
In my mind, there wasn’t much the residential market could throw at me. I should have guessed something was up by the half-amused look on my customer’s face when he described the problem as “a real hair raiser,” and that a measure of caution was in order … but what could be dangerous about a small furnace?
This article is part one of a two-part series on ice flake
machine troubleshooting. This article will examine troubleshooting low and high
water levels. Next month’s article will examine water impurities and mechanical
There’s a new tekkie product on the market almost every day - or so it seems. And the HVAC trade is certainly not immune to a deluge of new products, be they mobile for field applications or computer software/web portals for office workers. This article offers a glimpse of a potpourri of software and related products.
This article explores how a restricted metering device will affect system performance and efficiency. The system is a commercial refrigeration system with a TXV as the metering device. The refrigerant being used is HFC-134a. Very similar results will occur if an automatic expansion valve (AXV) is used.
The actual frequency and tasks performed will vary from system to system. However, here are some generic maintenance tasks which can be applied to many refrigeration systems. These tasks can be divided into two groups: one for maintaining the cabinet and one for maintaining the refrigeration system.