This article is part two of a two-part series on ice flake machine troubleshooting. The last article, which appeared in the Feb. 7 NEWS, examined troubleshooting low and high water levels. This article will examine water impurities and mechanical problems.
Air conditioning coil cleaning is an important air conditioning maintenance procedure that sometimes takes some patience, and usually takes a lot of water. First, you have to make some common sense evaluations.
Bob and Btu Buddy were on a service call yesterday where the compressor motor was running overloaded due to internal load; the bearings were dragging or worn. Btu Buddy told Bob, “Motor overload protection and circuit protection are subjects that need to be discussed later.” They’ve gotten together today for that discussion.
My Feb. 7 column focused on ice flake machine troubleshooting. I will have more to say on that specific topic in my April 4 column. For this column, I want to take a look at amperage as it relates to HVACR compressors.
In this month’s troubleshooting situation, our customer has called to say that the older package unit that heats and cools his office is managing to warm up the area, but then seems to cool down too much before providing heat again. When you arrive, the first thing you note is that the indoor blower motor is operating, and you check the fan switch setting on the thermostat.
Bob got a call from the dispatcher to go to an office building that has a 3-ton heat pump compressor that has been shutting off after startup. The fan would continue to run. The building maintenance man said that he had observed the shutting down of the compressor several times.
This article is part one of a two-part series on ice flake
machine troubleshooting. This article will examine troubleshooting low and high
water levels. Next month’s article will examine water impurities and mechanical
Bob has gone on a service call where the customer is complaining that her house is not getting up to temperature. The house was heated with a heat pump with three stages of auxiliary strip heat. Bob removed the panel to the strip heat and found one of the units was not pulling current.
This troubleshooting situation is a look ahead to the upcoming cooling season. Our customer has called to say that their heat pump “isn’t cooling at all,” and while the outdoor temperature is only in the mid 80’s, it’s quite uncomfortable in the house. You find that the underlying reason is that the compressor and outdoor fan motor aren’t operating.