To prepare you for this month’s troubleshooting situation … you’re not the first technician to be called, nor are you the second technician. You’re the third one that’s been called in to solve this customer’s problem, which involves a heat pump that serves a residential building in a mild Southwest desert climate.
Tim and Bob have been sent on a service call to a new customer’s house. The homeowner has an unusual complaint. She said that she thinks she has a furnace problem because there is mold in her house. They don’t know what this can be all about.
Bob and Tim have arrived back at the apartment building where they have been working for several days inspecting and making necessary repairs to the building’s split-system heat pumps. Bob said, “Check the list for another unit that seemed to have a problem and let’s take a closer look at it.”
In this situation we have a customer who has called for service on their gas furnace, and the description of the problem is “no heat at all.” The customer also reports that this is the first time they’ve had to call for service on their 10-year-old unit.
Many servicemen experience service calls where the compressor has both a low head pressure and a high suction pressure. There are three main reasons why a compressor will simultaneously have a low head pressure and a high suction pressure.
Bob and Tim have arrived at the apartment house that they have been working at for the last several days. They’ve gone to the roof where the outdoor units are located. There are 60 heat pumps that use R-22 as the refrigerant. They start with Unit No. 2.
Bob and Tim are on the second day of an inspection of an apartment house building that has multiple split-system heat pumps. They have inspected all 60 outdoor units on the roof. They are now going to inspect the indoor units.