Bob and Tim have been sent on a routine service contract call to a new customer. The system is a gas furnace with central air conditioning. After changing the filter and oiling the fan motor, Tim went to the thermostat and caused the furnace to come on and they were looking at the burner when Tim said, “That gas flame doesn’t look right.”
In this month’s troubleshooting situation, we have a customer who has called to say that their condominium has no heat. The particular equipment in this case is a thru-the-wall package unit that provides cooling in the summer and employs a natural gas system to heat the building in the winter.
Ideal for professional preventive maintenance and troubleshooting applications, the 160x120 thermal imager is an addition to the Test and Measurement line and M12™ Lithium-Ion system, the company says.
Bob and Tim are continuing a service call on a heat pump that has two failed auxiliary heaters. When they went to the supply house to get new heaters, they left wondering if the heat pump itself was operating up to capacity. After replacing the defective heaters, Bob suggested a visual inspection of the heat pump.
Bob and Tim have arrived at a home where the owner is complaining that the heat pump is not heating properly. It has been getting cold in the home during the late night and early morning hours. It’s really cold outside, about 10°F at night and 25° during the day.
To prepare you for this month’s troubleshooting situation … you’re not the first technician to be called, nor are you the second technician. You’re the third one that’s been called in to solve this customer’s problem, which involves a heat pump that serves a residential building in a mild Southwest desert climate.
Tim and Bob have been sent on a service call to a new customer’s house. The homeowner has an unusual complaint. She said that she thinks she has a furnace problem because there is mold in her house. They don’t know what this can be all about.
Bob and Tim have arrived back at the apartment building where they have been working for several days inspecting and making necessary repairs to the building’s split-system heat pumps. Bob said, “Check the list for another unit that seemed to have a problem and let’s take a closer look at it.”
In this situation we have a customer who has called for service on their gas furnace, and the description of the problem is “no heat at all.” The customer also reports that this is the first time they’ve had to call for service on their 10-year-old unit.
Many servicemen experience service calls where the compressor has both a low head pressure and a high suction pressure. There are three main reasons why a compressor will simultaneously have a low head pressure and a high suction pressure.