Leo's HVAC Tips: Relative Humidity, Ventilation, And Turning Vanes
HumidityWe commonly use the term "humidity," but the proper term is relative humidity (rh). Relative humidity is the percent of moisture in the air relative to the moisture the air can hold at a specific temperature. When you see 50 percent rh it means that the air holds 50 percent of the moisture that it is possible to hold at that temperature. The higher the air temperature, the more moisture it can hold. This means that air at a temperature of 80 degrees F and 50 percent rh holds more grains of moisture than the same amount of air at a temperature of 60 degrees and 50 percent rh.
For a catalog of books that will tell you more about this subject, e-mail your name and postal address to firstname.lastname@example.org.
VentilationBe sure to provide the amount of ventilation air set by codes. Insufficient ventilation can create health problems.
Adapted from Indoor Air Quality from the Indoor Environment Technician's Library series, www.lamabooks.com.
Turning VanesSquare throat elbows must have turning vanes to reduce dynamic loss.
Double-wall turning vanes were commonly used in the past. However, research has shown that these are less effective than single-wall vanes.
Single-wall turning vanes produce the smallest amount of dynamic loss. A single-wall turning vane should have a trailing edge. This will further reduce dynamic losses.
Adapted from Airflow in Ducts by Leo Meyer, from the Indoor Environment Technician's Library series, www.lamabooks.com.
Publication date: 09/26/2005