ARI Posts Addendum To Standard 550/590
The standard and addendum can be downloaded for free at www.ari.org (website).
Standard 550/590-98 combines two previously separate standards: ARI Standard 550-92, “Centrifugal and Rotary Screw Water Chilling Packages,” and ARI Standard 590-92, “Positive Displacement Compressor Water Chilling Packages.”
In 1999, ARI’s Large Tonnage Liquid Chiller Product Section voted to combine the two standards to reduce confusion in equipment application and ensure consistent treatment for rating and testing of two similar and overlapping product lines.
The combined, revised standard includes two other major changes that affect how chillers are rated and tested. These changes relate to the integrated part-load value (IPLV) and the fouling factor adjustment used for evaporators in closed-loop water systems.
The IPLV rating conditions and part-load weightings have been changed to more closely reflect actual operating experience found in the field for a single chiller. The evaporator fouling factor has been changed from 0.00025 to 0.0001 based on research work sponsored by the American Society of Heating, Refrigerating, and Air-Conditioning Engineers (ASHRAE), which, according to ARI, shows that the actual fouling of the waterside of evaporators operating in closed-circuit water systems experience very minimal degradation in performance over time.
Publication date: 08/05/2002