# Sizing Walk-in Coolers And Freezers

June 2, 2002
 Email / Print / Reprints / / Text Size+
Sizing walk-in coolers and freezers generally is not a difficult procedure. Many reference charts list the required refrigeration loads for different size walk-ins. Generally, they provide two load estimates — one for average usage and one for heavy usage.

Remember that these load calculations are only estimates. The actual load requirements for a particular walk-in cooler or freezer may differ.

Most load calculations for any walk-in cooler or freezer are based on four separate loads, including:

1. Heat transmission — heat gained through the walls, floors, and ceiling of a walk-in structure;

2. Air infiltration — heat gained due to the air entering the structure;

3. Product load — heat removed from a product to cool it from one temperature to a lower temperature; it also includes the heat of respiration from some fruits and vegetables; and

4. Supplemental loads — heat dissipated by people or mechanical equipment in the walk-in.

The person sizing a walk-in cooler or freezer must understand the application and environment in which the walk-in will be used. There are several situations where a person relying on the sizing chart alone could miscalculate the actual load for the walk-in.

If, for example, the walk-ins were to be located outdoors rather than indoors, the heat gain through transmission would be much greater in the hot days of summer than normally accounted for in many sizing charts. The size of the refrigeration equipment may need to be increased to satisfy this additional load.

A person sizing a walk-in cooler or freezer should ask these two important questions:

1. Where is the walk-in going to be installed?

2. What will the maximum ambient temperature be outside of the box?

## PRODUCTS

Other important questions to ask concern the product going into the walk-in:

• How much and what type of product will be stored?

• What is the initial temperature of the product entering the walk-in?

• At what temperature does it need to be stored?

Again, most charts are based on averages. If the temperature of the product entering the walk-in is higher than normal, or if an unusual amount of product will be stored in the walk-in, the capacity of the refrigeration equipment may need to be increased. Another potential problem with using generic sizing charts is with supplemental loads. If the supplemental load is higher than the averages, the capacity as listed on a generic chart may need to be increased. For example, if many people will be working in the cooler, or if some type of major equipment will be running in the walk-in on a consistent basis, the load may need to be increased.

Any person sizing walk-in coolers and freezers should determine if a particular application falls outside the loads as stated on the charts, and if a complete load calculation needs to be done.

Marchese is owner of Coldtronics, Pittsburgh, PA; 412-734-4433; www.coldtronics.com (website); joe@coldtronics.com (e-mail).

Publication date: 06/03/2002

## Image Galleries

### 2015 HARDI Fly-In

Highlights from HARDI's Congressional Fly-In in Washington, D.C.

## Podcasts

Clint Schreck, general manager, Columbus Worthington Air, Columbus, Ohio, discusses winning Angie’s List Super Service Award, how to handle online reviews, and much more.

More Podcasts

## 2015 May 25

Check out the weekly edition of The NEWS today!

### HYDROCARBON REFRIGERANTS

The EPA has approved several hydrocarbon (HC) refrigerants for HVACR applications. Do you support the use of HCs?
View Results Poll Archive

### HVACR INDUSTRY STORE

2015 National Plumbing & HVAC Estimator

Every plumbing and HVAC estimator can use the cost estimates in this practical manual!

More Products

### Clear Seas Research

 With access to over one million professionals and more than 60 industry-specific publications, Clear Seas Research offers relevant insights from those who know your industry best. Let us customize a market research solution that exceeds your marketing goals.