What You Need to Know About Motor Speed
Every motor has magnetic poles, just like a permanent magnet. These poles are created by bundles of magnet wire wound together in the slots of the stationary part of the motor (the stator core).
Look inside an electric motor and you can count the number of poles or windings (see the photos that accompany this article). The number and alignment of these bundles of wires creates magnetic poles, and the number of poles in the motor determines the motor’s speed, stated in revolutions per minute (rpm).
Keep in mind, no-load rpm is a factor of motor poles and power frequency, not voltage, horsepower, or motor diameter.
With that knowledge in mind, you may surmise that every four-pole ac induction motor runs at the same speed. This is in fact the case. You can determine this speed by using the following formulas:
For 60-Hz electrical systems — 7,200 divided by the number of poles gives you the no-load rpm.
For 50-Hz systems — 6,000 divided by the number of poles gives you the no-load rpm.
(For the purpose of this article, I’ll use the North American [60-Hz] system.)
Another important element to remember from this formula is that I’ll be giving you the no-load rpm in the following examples. You should note that under load, the rotating parts of the motor fall behind, or “slip,” the magnetic speed.
Motor Types, ApplicationsUsing the standard formula, you can determine that a four-pole motor operating under no-load conditions will run at 1,800 rpm (7,200 divided by four poles). Loaded, the motor will slip to between 1,600 and 1,750 rpm. Four-pole designs are the most common pole configuration for ac induction motors and are typically found in belted applications such as blowers, fans, air-handling equipment, compressors, commercial garage door openers, and conveyors.
A two-pole motor will operate at 3,600 rpm unloaded and between 3,000 and 3,450 rpm under load. Such speeds are commonly found in pump applications, such as submersible pumps, sump pumps, and pool or water recirculating equipment.
Another typical application is small ventilating fans. To the untrained ear, two-pole motors appear to need servicing because they sound somewhat noisier when running. This is principally due to the higher rpm. As a service technician, you should be aware of the different “normal” sounds a motor makes that are related to speed.
Six-pole motors run at 1,200 rpm unloaded and between 1,050 and 1,175 rpm loaded. They are often used for air-handling equipment, direct-drive applications, window fans, furnace blowers, room air conditioners, heat pumps, residential garage door openers, and other equipment.
As you can imagine, lower mechanical speeds often result in quieter designs, which makes an eight-pole motor well-suited for many residential applications where noise is a factor. These motors operate at 900 rpm unloaded (between 800 and 875 rpm loaded), and are being used more extensively today in room air conditioning, outdoor heat pumps, and residential garage door openers.
A less common design is the 12-pole motor. This motor, which runs at 600 rpm unloaded, is used in washing machines and other equipment that requires a slow cycle.
Pole to PoleHere’s the important point to remember: When replacing a motor, you must select a replacement with the same number of poles as the original.
In changing, say, from a four-pole to a six-pole design, the speed mismatch is likely to create significant problems.
Now that you understand the principles behind motor speed, you’re ready to learn about multispeed motors and their uses. That will be tackled in a future Motor Doctor article.
Simon, The News’ “Motor Doctor,” is with A.O. Smith Corp., Milwaukee, WI; 414-359-4104; 414-359-4064 (fax).
Publication date: 06/25/2001